for Wilberforce, OH
I Pulled inducer motor and cleared water out of motor as well as cleared the drain lines. Condensate trap was found to be clogged causing water to back up into motor. The Access water wouldn’t allow motor to get to the required rpm needed to pull in pressure switch. Cleared condensate trap reinstalled trap and inducer motor reattached pressure switches and restarted system.
I found the inducer motor was broken, I recommended the customer replace the inducer motor, said he would get back to me.